There are two key standards for control panels within IEC standardization:
Whereas IEC 61439-1 describes the options for verifying short-circuit strength in detail, IEC 60204-1 does not include any verification procedure. Other standards such as IEC 61439-1 are referenced as an option; this includes a note to the effect that the planner is free to decide whether, in addition to the requirements of IEC 60204-1, they take into account the relevant parts of the IEC 61439 series for particular elements of the electrical equipment, depending on how the machine is used and what electrical equipment it has.
As far as the IEC 61439-1 standard is concerned, there are two methods for verifying short-circuit strength:
An inspection is therefore a prerequisite in both cases, either of parts of the control panel or the control panel in its entirety.
Note: Siemens offers comprehensive, proven reference designs for carrying out verification by comparison, depending on the structure of the circuits of the switchgear and controlgear assembly in question. You can find these in the "Siemens Industry Online Support" (SIOS) by searching for "Short-circuit ratings as a function of minimum enclosure size in accordance with IEC 61439-1".
Note: The free "SIMARIS curves" software tool from Siemens contains a wide range of overcurrent protective devices including all key characteristics. The tool can be used to not only determine, but also to easily document the let-through value for the relevant short-circuit current.
It looks like you are using a browser that is not fully supported. Please note that there might be constraints on site display and usability. For the best experience we suggest that you download the newest version of a supported browser: