How to efficiently calculate the Short-circuit capacity of your control panel?
Have you ever had the need to comply with the requirements 50kA or 25kA control panel? How accurate is this actually? How does it impact your design, your engineering time and therefore the costs?
The challenges regarding cost pressure in electrical engineering and control cabinet construction are enormously high, and the calculation of short-circuit current influences tremendously the cost of the solution.
Please use another Browser
It looks like you are using a browser that is not fully supported. Please note that there might be constraints on site display and usability.
For the best experience we suggest that you download the newest version of a supported browser: